Folks living in the colder climes often find that carrying out the sump pump testing procedure produces some movement in the sump water but no discharge from the pipe. While it is possible that there may be debris inside the pump that is causing the blockage or the sump pump's plumbing itself has frozen, most such cases occur because the water in the discharge pipe has frozen and thus blocked the exit. While minor blockages can be mildly annoying, complete blockages are dangerous.
First, these blockages force the pump to run continuously without removing any water and can thus cause pump burnout. Further, as water collects in the sump, the pump may overflow and flood the basement. To ensure your basement and pump don’t fall prey to frozen pipes and the pump itself doesn’t freeze, we’ve provided a short guide for learning how to avoid a frozen sump pump.
- 1 Can sump pump pipes freeze?
- 2 Make Use of the Gradient
- 3 Use a wide/large pipe
- 4 Keep Workload Low
- 5 Reducing Pump Workload
- 6 Heat the Sump Water
- 7 Freezing of Internal Pump Components
- 8 Important Notes
- 9 Frequently Asked Questions
- 10 Conclusion
Can sump pump pipes freeze?
Yes, they absolutely can! If the temperature outside gets too cold it is possible for your sump pump pipes on the exterior to freeze, and any standing water that is left in them will eventually freeze too! If your sump pump begins running but never actually removes any water from your sump basin it is likely that your pipes have frozen and you may need to review the tips below on how to correct the problem.
Make Use of the Gradient
Freezing occurs mostly in the section of the pipe that sits outside the house and is thus exposed to the elements. While such exposure is inevitable, its effects on the water inside the discharge pipe are magnified if the water is not allowed to exit the pipe easily. This happens when the pipe’s angle does not match that of the slope of the ground.
If you are learning how to use a sump pump, you can simply attach the pipe in a manner that obeys the gradient of the ground around your house. If you have already installed the pipe, you may need to disconnect the pipe and then choose one that is capable of following the slope correctly.
Use a wide/large pipe
When you disconnect the old pipe, you may consider using a large/wide pipe ie one with greater internal diameter, as the replacement. Ideally, this enhanced diameter should be much higher than that needed to remove even the highest amount of water during the monsoon. If you’re wondering how a large pipe is linked to learning how to avoid a frozen pipe, let us add that a large pipe is never likely to be full of water.
As such, even if the water is not drained out at any point of time and freezes due to the cold weather, it would not create a complete blockage. Further, because water tends to flow out of any possible opening, the very fact that the pipe never completely fills up with water at any point acts as a means of ensuring that any water that is left over flows out of the pipe over time instead of freezing inside the pipe itself.
Keep Workload Low
While it may not be possible to reduce the sump pump’s workload in emergency situations, it is possible to take precautions beforehand that ensure that in cases of freezing inside the discharge pipe, the pump does not have to work itself to exhaustion. This is all the more important because when the pipe is partially blocked, pumping out the same amount of water requires greater effort and this can put undue pressure on the pipe even when the water in the sump appears to be well within operating limits.
Reducing Pump Workload
Carry out regular sump pump maintenance to ensure collection of debris does not reduce the efficiency of the motor.
Consider using a backup sump pump in addition to the primary one.
Keep the maximum head (height to which water is raised) low so that the pump can remove water faster and with less effort.
Heat the Sump Water
In case of freezing in the pipe or in the sump itself, it is advisable to use a heating rod to heat the sump water to a lukewarm temperature. Make sure to install the heater low enough in the sump pump basin so that after all the water is drained the heating element is still submerged in water, running a water heater in the air can damage it.
- Disconnect the sump pump power supply.
- Remove the sump cover and note whether the sump water’s surface has completely frozen over. In case it has, use an ice pick to break the ice.
- Ensure that the sump pump has proper electrical insulation and grounding. If either is absent, follow the alternative steps outlined after this set of steps.
- Lower the heating coil/rod into the water. Ensure that it doesn’t rest against either the sump boundary or any sump pump component. Ideally you should hold the coil in place.
- Connect the coil’s power supply and start it. Use a thermometer to measure the temperature of the water in the sump.
- When the water temperature has risen by about 20-30 degrees Celsius, stop the coil and remove it
- Reconnect the sump pump power supply and wait for a while. The hot water would melt the ice in the sump and the pipe and this in turn would make water flow normal, at least for the time being. If your pump is not properly insulated, DO NOT lower the coil into the water.
- Instead: Heat water in a bucket using the coil.
- While the water heats, break any ice that may be lying on the top of the water in the sump.
- Once heating is complete, unplug and remove the coil.
- Pour the hot water from the bucket gently into the pump until about 1/4th of the sump remains above the water level.
- Start the sump pump and wait for the hot water to melt the ice.
- Once the sump pump has removed some of the water, pour out some more hot water. You may reheat the water still in the bucket if it has become cold.
Freezing of Internal Pump Components
Freezing of the sump pump itself is extremely rare since the oil inside the motor chamber is insulated from changes in outside temperature and freezing in the discharge or impeller can be removed using the above method. If you do suspect freezing of the core components of the pump or wish to learn how to avoid a frozen sump pump, you can:
Remove the pump from the sump after disconnecting the power supply.
Check for frozen water inside the impeller or discharge. Use an ice pick or similar instrument to remove such ice or frozen debris. If nothing is frozen, you can check for blockages that might freeze over during the winter.
Move the float gently to ensure that there is no jamming due to freezing. If it does not move easily, remove ice or debris from the shaft and/or the float itself till movement becomes normal.
Note whether the insulation of the motor compartment has been damaged anywhere. Such damage may have led or in the future may lead to the motor lubricant oil or coating oil freezing over.
Leave the sump pump in a warm area for some time. You can also leave it near a heat source that does not involve flames. Even if there is no actual freezing, this step would help melt any blockages within the pump that might freeze later. Replace the pump in the sump and check whether the pump is working normally.
Note: Never try to heat the pump or any of its components directly as this may lead to the motor exploding or the lubricating oil catching fire.
Avoid pouring water too fast. If too much hot water interacts with cold water, excess steam may be produced. While not harmful, such steam may reduce visibility and force you to stop the process.
There is no need to empty the bucket into the sump. Once you feel the pump is able to remove water at a normal pace, it is time to stop the process.
Sump pumps are not designed for working with extremely hot water. Heating water too much might ruin the internal components of the sump pump.
Do not touch the water with your hand while the coil is in the sump. In fact, you should wear rubber gloves while lowering the thermometer or use a non-conducting stick to check the temperature. If you don’t adhere to these requirements, you may get a nasty electrical shock!
Frequently Asked Questions
What to do if your sump pump line is frozen?
If the line is frozen, use portable heaters to thaw it. Don't risk hurting yourself or damaging property by using a blow torch because you can easily damage either one! If there's no way for someone who knows what they're doing on site with these tools then call in professionals immediately-it might just be too late otherwise
Can sump pump discharge freeze?
When winter comes along, your sump pump is designed to keep all excess water out of the basement. But if that line has frozen over with ice layers on top then you're left vulnerable and susceptible for any potential damages caused by an errant slab leak or other emergency situation happening at anytime during these cold months!
Can you unplug sump pump in winter?
No, you should never unplug your sump pump or you will risk flooding in your home! Unplugging your sump pump over the winter is asking for trouble. While you might think that it won't be necessary, a warm front can come through and cause melting snow or rain which will fill up any basements left unchecked by plugs from last year's rains before they've had time to drain away on their own accord- leading once again towards possible flooding in homes across America!
How do you insulate an outside sump pump?
The best way to insulate an outdoor sump pump is by covering the pit with some naturally occurring material that provides some way to trap heat and prevent the cold from getting in. The best practice is to cover the pit with a tarp and then put hay on top, the hay will act as a natural barrier that is hard for cold air to penetrate.
What happens if a pump freezes?
When your pump freezes it could become damaged or even worse could end up creating a leak somewhere in your plumbing that will not be evident until the weather starts warming up and things begin thawing out. Because water expands when it freezes it could end up overpowering your plastic PVC piping which is only rated to hold so much pressure.
How do I know if my sump pump is frozen?
The easiest way to test if your pump is frozen is to look for signs of flooding or see if your pump basin water is not leaking out. If your pump is constantly running it could mean the water level is never decreasing which could be due to a large clump of ice right at the discharge line. Another quick test is to bypass your float switch completely and plug the pump right into the wall, then check to see if water is being removed from your basin.
Freezing is not included among the most common sump pump issues and solutions because it affects only those in particular climatic situations and that too, not very often. However, if you do find your sump pump or any of its components frozen, it is advisable carry out the above procedures and so ensure that as and when the rains come, your pump is ready to handle them. On the other hand, if you believe the pump can freeze sometime in the future and would like to learn how to avoid a frozen sump pump, you should assess the possible threats to your pump and discharge pipe during the autumn or early winter so as to give yourself adequate time to carry out the necessary procedures.